Change notes for IBM IBM Switched & Monitored PDU Firmware, version 1.08.0003
Items one through five below were changed because of known bugs.
Fixed the SNMP trap cold boot issue when warm boot.
Fixed the SNMP getbulk issue when use MG-Soft walk command 3. Fixed the wrong description in the SNMP v3 security level help screen 4. Fixed when set external temperature or humidity critical threshold through SNMP, NMC will clear external temperature or humidity warning threshold to 0.
Modified SNMP reportFlag set to 0
Items 6 through 14 below were changed because of additional AEM functionality requested by IBM. Some of these do not work unless the optional external temperature and humidity monitor are attached to the PDU. Unsupported entries will return 999 for the value.
Added the ibmPduReboot: “Set 1 to reboot PDU”.
Added the ibmPduOutletGlobalDelayTimer:”Global delay timer for all outlets.Range:0 sec~3600sec.Default value :0 sec. To combine with Individual Delay timer to control outlet state/behavior as rack power on or restore” 8. Added the ibmPduOutletIndividualDelayTimer:”The delay timer for each outlet as AC power restored.Range:0 sec~ 3600 sec. Default value:0 sec. To combine with Global Delay timer to control outlet state/behavior as rack power on or restore” 9. Added the ibmPduPhaseLastPowerReading:”The value of the most recent power reading for this phase, in watt” 10. Added the ibmPduThermalLastReading:”The value of the most recent temperature reading for the internal temperature sensor, in degrees Celsius” 11. Added the ibmPduHumidityLastReading:”The value of the most recent humidity reading for the internal humidity sensor, as a percetage” 12. Added the ibmPduOutletLastPowerReading:”The value of the most recent power reading for this outlet, in watts” 13. Added the ibmPduExtThermalLastReading: The value of the most recent temperature reading for the external temperature sensor, in degrees Celsius. If no external temperature sensor is connected, a value of -1 should be returned.” 14. Added the ibmPduExtHumidityLastReading:” The value of the most recent humidity reading for the external humidity sensor as a percentage. If no external humidity sensor is connected, a value of -1 should be returned.”
To view PDF files you must have the latest version of Adobe Acrobat installed on your system.